ACI delivers winter warning on arctic grade flexibles
Doncaster Cables fully supports the Approved Cables Initiative (ACI) and its aim to investigate, address and remove unsafe, non-approved and counterfeit cables from the UK market place. We would like to take this opportunity to relay a warning recently published by the ACI.
The article can be found in the news section of the ACI's website however the content of the article has been copied in full below.
Monday 18th of December 2017
With the UK having already experienced some severe winter weather, the Approved Cables Initiative (ACI) is advising contractors and distributors to check their cable choices carefully following the discovery of significant quantities of substandard arctic grade flex.
Recent market surveillance has detected failures on numerous examples of arctic grade flexibles including pre-assembled industrial hook-up leads. These samples were purchased from a variety of sources including electrical wholesalers, DIY stores, online retailers and eBay stores.
Major concerns arose when ordinary duty flexibles (designed for indoor use to +5°C) were discovered coloured yellow, in what could be interpreted as a deliberate attempt to pass the cable off as an arctic grade flexible (designed for use at sub-zero temperatures and tested down to -40°C).
The pre-assembled yellow leads, sold as industrial extension leads designed for use in harsh environments, incorporated cable clearly marked as H05VV-F (ordinary duty flexible). When subjective to the cold bend test as an arctic grade flexible the cable failed to maintain its integrity; the sheath split open and insulation cracked, subsequently exposing what would be live copper conductors.
Arctic grade cable, which is predominantly yellow or blue in colour, is often used on construction sites and by caravan and motorhome owners to provide temporary outdoor power supplies and in some indoor applications such as cold stores.
Whilst it is normal to have different colours of H05VV-F flexibles (such as white, black, orange and gold), yellow and blue are commonly associated with arctic grade flex and these substandard products could lead end-users to use cable unsuitable for their intended purpose.
Suppliers and end users, who need cable suitable for outdoor use in the cold, should look for the cable marking 'BS 6004' and the UK cable code for arctic grade cable, such as '3183A'. Cables marked with 'H05VV-F' are not intended to be suitable for such use.
In the past month, several new examples of substandard arctic grade flex have been found which are currently undergoing further testing.
Previous independent testing of arctic grade flex samples has shown cables exhibiting poor conductor resistance with sheathing and cable insulation disintegrating when subjected to a cold bend test. This problem could result in a fire, short circuit or an electric shock.
Peter Smeeth of the Approved Cables Initiative said: "The harsh environment in which these cables should operate means they need to be able to withstand forceful treatment and contractors need to know their cable choice is safe and suitable for its application. Having originally warned of such issues six years ago it is worrying to see a marked increase in substandard artic grade cable again.
"The ACI continues to monitor the market place but we need distributors and contractors to check their stocks and ensure their cables comply. They should look for cable markings and third party independent approval of all purchases. If they are in any doubt about a cable they should contact the Approved Cables Initiative immediately."
For further advice on this issue and other substandard cable call 0208 946 6978/07973 636688 or email